These are methods approved by Suburban for maintaining a Suburban Water Heater. All of the methods are proven and should be followed to maintain the integrity of the water heater and protect it’s warranty if it is new. There is a lot of differing information available and some of it might have it’s place but, Suburban does know best!
Can I operate my water heaters electric element and gas burner at the same the time?Yes, when taking advantage of available campsite or generator-produced electricity you may operate on both gas and electric for a faster recovery rate
Are all water heaters equipped with an Anode Rod? What is its function? When should it be changed?
Only Suburban water heaters feature an anode rod. The anode equalizes aggressive water action, providing cathodic protection for the tank. It is a very important factor in tank life and should only be removed for inspection, draining or replacement. It is removable using a 1-1/16″ thin wall socket.
Why does water drip from my water heater’s pressure and temperature (P&T) relief valve?
You may experience water weeping or dripping from your water heater’s pressure and temperature (P&T) relief valve when your water heater is operating. Water weeping or dripping does not mean that the P&T valve is defective. As water is heated, it expands. The water system in a recreational vehicle is a closed system and does not allow for the expansion of heated water. When the pressure of the water system exceeds the relieving point of the P&T valve, the valve will relieve the excess pressure.
• One way to reduce the frequency of this occurrence is to maintain an air pocket at the top of the water heater tank. This air pocket will form in the tank by design – however, it will be reduced over time by the everyday use of your water heater. To replenish this air pocket:
I noticed an add-on electric element for my water heater. What will happen if I use it?
Any alterations to a Suburban water heater will void its warranty. This includes add-on electric aftermarket heating elements. There are a number of heating elements being offered. These elements are supplied with different types of thermostats which are mounted in various locations of the water heater. These heating elements can lack critical safety controls. Use of these devices can lead to an out of control heating of the water tank and a catastrophic wet side explosion. The use of these aftermarket heating element devices may result in damage to components or the water heater. When aftermarket heating elements are inserted into the anode rod/drain connection, tank life is shortened by accelerating inner tank corrosion. This will be a non-warrantable situation.
There is a bad odor coming from the hot water faucet. How can I correct this?
Odor from the hot water system is not a service problem and many water supplies contain sufficient amounts of sulphur to produce an odor. The odor is similar to rotten eggs and is often referred to as “sulphur water.” Sulphur water is not harmful – only unpleasant to smell. Sulphur water can be caused by a chemical action or by bacteria.
The key to eliminating this smell is heavy chlorination of the water system. Add about six (6) ounces of chlorine (common household liquid bleach) to each 10 gallons in the water tank. Then run the heavily chlorinated water throughout the system, opening each faucet one at a time until you smell the chlorine. Let the RV sit a few days and the chlorine should take care of the problem. Then you will need to take care of the chlorine by flushing the water system. If you don’t have a water filtration system that removes chlorine, you may have a problem getting rid of the chlorine taste. You might consider adding such a system because it allows you to keep water chlorinated and this prevents several problems, including sulphur water. Chlorination also takes care of other types of bacteria and viruses.
How do I drain my water heater?
- If the RV is to be stored during winter months, the water heater must be drained to prevent damage from freezing:
Are there any tips for winterizing my water heater?
If your water heater plumbing system is equipped with a bypass kit, use it to close off the water heater. Drain the water heater completely and leave it closed off (out of the system) in the bypass position, particularly if you are introducing antifreeze into the plumbing system. Antifreeze can be very corrosive to the anode rod. The result will be accelerated deterioration of the rod and heavy sediment in the tank. If the plumbing system is not equipped with a bypass kit and you intend to winterize by adding antifreeze into the system, remove the anode rod (storing it for the winter) and replace it with a 3/4″ drain plug.
How do I get an owner’s manual for my water heater?
You can contact Suburban via written correspondence, phone, e-mail with your model and serial number of the appliance. The Manual can be e-mailed as a PDF file or mailed out in printed form.
What if I operate the water heater without water in the tank?
Operation without water in the tank on the 12 VDC gas portion of the water heater can cause the copolymer insulation jacket to melt and can cause the ECO/Thermostat to trip. Operation without water in the tank on the 120 VAC electric portion of the water heater will damage the element.